This article has Open Peer Review reports available.
Legionnaires’ disease case-finding algorithm, attack rates, and risk factors during a residential outbreak among older adults: an environmental and cohort study
© Silk et al.; licensee BioMed Central Ltd. 2013
Received: 22 December 2012
Accepted: 20 June 2013
Published: 27 June 2013
During a Legionnaires’ disease (LD) outbreak, combined epidemiological and environmental investigations were conducted to identify prevention recommendations for facilities where elderly residents live independently but have an increased risk of legionellosis.
Survey responses (n = 143) were used to calculate attack rates and describe transmission routes by estimating relative risk (RR) and 95% confidence intervals (95% CI). Potable water collected from five apartments of LD patients and three randomly-selected apartments of residents without LD (n = 103 samples) was cultured for Legionella.
Eight confirmed LD cases occurred among 171 residents (attack rate = 4.7%); two visitors also developed LD. One case was fatal. The average age of patients was 70 years (range: 62–77). LD risk was lower among residents who reported tub bathing instead of showering (RR = 0.13, 95% CI: 0.02–1.09, P = 0.03). Two respiratory cultures were characterized as L. pneumophila serogroup 1, monoclonal antibody type Knoxville (1,2,3), sequence type 222. An indistinguishable strain was detected in 31 (74%) of 42 potable water samples.
Managers of elderly-housing facilities and local public health officials should consider developing a Legionella prevention plan. When Legionella colonization of potable water is detected in these facilities, remediation is indicated to protect residents at higher risk. If LD occurs among residents, exposure reduction, heightened awareness, and clinical surveillance activities should be coordinated among stakeholders. For prompt diagnosis and effective treatment, clinicians should recognize the increased risk and atypical presentation of LD in older adults.
Legionnaires’ disease (LD) is a potentially-fatal pneumonia caused by inhalation of water aerosols containing Legionella bacteria. In the United States, ~8,000-18,000 persons with community-acquired LD are hospitalized annually . Annual incidence rates of LD increase with age to more than ~1.6 cases per 100,000 among persons ≥65 years old [2–4] and LD-related mortality is higher among older adults compared with younger persons . Immunosenescence contributes to the disproportionate burden of LD among the elderly. Also, certain medical conditions known to increase the risk of acquiring LD, including chronic lung disease, lung cancer, hematologic malignancies, end-stage renal disease, diabetes mellitus, and immunosuppression , are more prevalent in older persons . Swallowing difficulties, which are more common in the elderly, further increase the risk of lung inoculation through aspiration.
Most LD cases occur sporadically; relatively few patients with LD are diagnosed and reported to public health officials . Therefore, detection of a LD outbreak creates important opportunities for prevention through the elimination of transmission sources and colonization reservoirs in community and residential settings and opportunities for prompt, effective treatment of individuals infected during an outbreak [7, 8]. LD outbreaks among residents of long-term care facilities and nursing homes have been publicized and described elsewhere . However, few published reports have described LD outbreaks in apartment buildings and other residential facilities designed for seniors who live independently, even though these facilities are increasingly common in the United States [10, 11].
On October 15, 2009, the Baltimore City Health Department and the Maryland Department of Health and Mental Hygiene contacted the Centers for Disease Control and Prevention (CDC) regarding an outbreak of LD among residents of an apartment complex for seniors in Baltimore. In the previous 5 weeks, four residents and a visitor to the complex had been hospitalized with LD. One patient had died and another was receiving intensive care. We investigated to find additional cases, identify exposures associated with disease transmission, determine the source of Legionella colonization (if any) at the complex, and recommend interventions to prevent additional cases.
Epidemiological and environmental investigations were conducted at the apartment complex, which consisted of four adjacent buildings. Two buildings were built in 2004; the third and fourth buildings were built in 2006 and 2009, respectively. Occupancy of the buildings began soon after construction of each was complete. An age of 62 years or older was required for residency. Single residents occupied most (>90%) of the 340 apartment units at the complex and virtually all units were occupied by October, 2009. Common areas were available to residents (e.g., communal kitchens, laundry facilities, and public restrooms). Medical services were not available onsite, but communal meals and social gatherings occurred regularly.
For case finding, we defined confirmed cases of LD as a diagnosis of clinical or radiographic pneumonia and laboratory-confirmation of LD (i.e., urine antigen testing, culture identification of Legionella from respiratory secretions, or a four-fold increase in serum antibody titer to L. pneumophila serogroup 1) between August 1, 2009 and December 31, 2009 among a resident of any apartment building in the complex. Possible cases were defined similarly, but had either incomplete (i.e., a single Legionella titer) or no specific laboratory testing for Legionella infection performed. Respiratory illnesses in persons with negative Legionella testing were considered non-cases.
To estimate attack rates and identify transmission routes, we conducted a retrospective cohort study among all 171 residents of the two affected buildings where LD cases had occurred (A-1 and A-2). The exposure period for the study was defined as August 1 through the date of survey interview. After informed consent was obtained, a standardized questionnaire was administered in person. We queried respondents about their demographic characteristics, water exposures at the complex and within the community, signs or symptoms of respiratory illness, healthcare use and diagnoses, smoking, and comorbid conditions (asthma; chronic lung, kidney, and liver disease; diabetes mellitus; heart disease or congestive heart failure; plus, immunocomprising conditions, including cancer, immunosuppressive therapies, human immunodeficiency virus infection, and organ transplant). Complaints about municipal water service interruptions and water quality (i.e., taste, smell, and appearance) were also recorded. We made at least two attempts on separate days to interview each resident; visitors were not included in the cohort study.
We maintained data in a Microsoft Access database (Microsoft Corp, Redmond, WA) and analyzed it in SAS version 9.2 (SAS Institute, Inc., Cary, NC). Attack rates (AR) for specific transmission risk factors (present vs. absent) were compared to calculate relative risks (RR) with 95% confidence intervals (95% CIs) and Fisher’s exact tests. A p-value less than 0.10 was considered statistically significant because of the small number of LD cases.
Our environmental investigation began with a physical inspection, noting the orientation of the apartment buildings, the design of the individual apartment units, and points of water use (e.g., showerheads, sink faucets) in each unit. Common areas where water exposures might have occurred were also noted. Diagrams of the potable water system were not available at this stage of the investigation.
On October 17, we collected 103 samples from five apartments of LD patients in affected buildings (A-1 and A-2) and three randomly-selected apartments of residents who had not developed LD in A-2 and each unaffected buildings (U-1 and U-2). (A resident of a randomly-selected apartment in A-1 developed LD after the apartment was sampled.) Specific sampling locations in the apartments included showerheads, sink faucets in kitchens and bathrooms, and water heater tanks (n = 56 samples). We also collected samples from outdoor fire hydrants (n = 6), from the buildings’ water intake valves (n = 19), and the sink faucets and water heating tanks of common areas in buildings A-1 and A-2 (n = 22). We collected samples of municipal water and expansion tanks, designed to absorb excess water pressure caused by thermal expansion or “water hammers” (i.e., water pressure surges), on October 21 and October 24, respectively. Biofilm swabs and one-liter bulk water samples were collected according to published procedures . Water temperatures and free chlorine concentrations (using N,N-diethyl-P-phenylenediamine reagents) were measured in potable water systems during this sampling.
At the CDC Legionella laboratory, bulk water samples were filtered through polycarbonate 0.2 μm filters. The filters were placed in 5 ml of sterile water and vortexed for 60 seconds. One hundred μl of this suspension were placed on buffered charcoal-yeast extract media with and without antibiotics. Plates were incubated at 95–98.6°F (35–37°C) in 2.5% CO2 to culture Legionella. We also forwarded two patients’ clinical isolates to CDC.
Serogrouping and determination of monoclonal antibody patterns [13, 14] were performed on all isolates. In addition, sequence-based typing was used to create seven-gene profiles (flaA, pilE, asd, mip, mompS, proA, and neuA) of the clinical isolates and select environmental isolates [15–17]. Sequence-based typing results were compared for clinical and environmental isolates to determine the source of the outbreak strain in the environment.
This study was determined an emergency public health investigation exempt from institutional review board (IRB) review; standard procedures to protect patient confidentiality were followed.
Demographics of residents and patients
Characteristics of Legionnaires’ disease patients among residents and visitors of an apartment complex for seniors
Exposures and disease transmission
Most (80%) cases were identified by urine antigen testing performed during hospitalization, with the exception of one case that was detected retrospectively ~47 days after illness onset (Figure 1). LD occurred among residents of buildings A-1 and A-2; no LD cases were detected among residents or visitors of the two other buildings (U-1 or U-2). Cohort study participation was high among residents of A-1 (86%) and A-2 (91%) (n = 143 respondents).
Legionnaires’ disease attack rates and relative risks among residents of an apartment complex for seniors (n = 143 respondents)
No. of LD patients
No. of non-patients
Relative risk*(95% confidence interval)
Potable water exposures
Any tub baths
Former (>100 cigarettes)
Chronic lung disease
Chronic kidney disease
3.33 (0.71– 15.70)
Although not included in the cohort, the two visitors who developed LD reported intensive exposures to water either during dishwashing (patient 4) or while cleaning the kitchen and bathroom using a bucket filled with water (patient 10) (Table 1); neither showered or bathed in the apartments. None of the residents with LD reported other known exposures to aerosolized water outside the apartment complex.
Environmental factors favoring colonization
The entire complex was served by the same municipal water system. Free chlorine residual was not detected in any bulk samples collected from showerheads or sink faucets during pre-remediation sampling. Each apartment had its own water heating tank. Free chlorine concentrations of 0.1 mg/dL were detected in three of the eight water heating tanks in patient and non-patient apartments. All water heaters had a factory temperature setting of ~120° F (~48.9°C), but temperature differences were observed in water collected from faucets at the bottom of tanks in sampled apartments (range: 70–100°F/21.1–37.8°C).
Three-quarters (75%) of residents who were interviewed noted at least one interruption in water service since August 1st. More than half of residents (56%) reported changes in the taste, odor, or color of their water during the same period.
Clinical isolates of L. pneumophila from patients 6 and 7 were characterized as L. pneumophila serogroup 1, monoclonal antibody type Knoxville (1,2,3). The outbreak strain was determined to be sequence type 222 (i.e., allelic profile 2, 19, 5, 10, 18, 1, 10).
Legionella culturing and monoclonal antibody testing of potable water samples collected from an apartment complex for seniors (n = 103 samples)
No. (%) positive
L. pneumophila1 (1,2,3)**
Affected buildings (A-1 and A-2) †
Water intake valves
Unaffected buildings (U-1 and U-2) †
Water intake valves
A large LD outbreak occurred at an apartment complex for seniors in Baltimore between September and December, 2009. Ten cases were confirmed among eight residents and two visitors to the complex; one case was fatal. Legionella respiratory cultures were available from two patients and characterized as L. pneumophila serogroup 1, monoclonal antibody type Knoxville (1,2,3), sequence type 222. An indistinguishable strain was detected in numerous potable water sources from apartment units of two buildings. Epidemiological data from a cohort study with a high response rate indicated that all patients were primarily or exclusively exposed to colonized potable water in apartments. Taken together, the environmental and cohort studies implicated Legionella colonization of the potable water system as the source of the outbreak.
The convergence of several factors led to the outbreak. Residents of the apartment complex were particularly susceptible to LD because of their advanced age, high prevalence of underlying conditions, and smoking habits. Although the size of the cohort limited statistical power, we confirmed that attack rates were highest in persons who smoked or had an immunocompromising condition. However, two younger visitors (including one without underlying risk factors) also developed LD. This finding suggested that the type, frequency, and duration of exposures may also determine disease risk. Also, the potable water system’s conditions were conducive to Legionella growth. Chlorine disinfection was not detected at the point of use in any of the residents’ apartments; hot water temperatures were generally within the ideal range for Legionella amplification (77°F-108°F/25°C-42.2°F). Importantly, the potable water system was colonized with a monoclonal antibody 2 positive , a virulent strain of L. pneumophila (sequence type 222) that has been previously associated with outbreaks in the northeastern United States and Canada [19, 20]. Nevertheless, the root cause of the outbreak was not determined conclusively during the outbreak investigation.
Increases in the burden of LD  may be related to the expanding population of older adults in the United States. Given the fact that a substantial number of residential facilities for the elderly exist [10, 11], facility managers, healthcare providers, caregivers, and local public health officials need to be aware of the potential for outbreaks among this population at higher risk for LD and LD-related mortality. Despite several published reports of LD outbreaks in nursing homes [9, 21, 22], this is the first published report of an outbreak at an apartment complex designed for elderly residents who live relatively independently.
Facility managers should consider developing a Legionella prevention plan in coordination with local public health officials as well as plumbers, engineers, or other environmental consultants. This plan may involve completing an environmental assessment to identify opportunities to reduce colonization risk . (A sample environmental assessment plan can be found here: http://www.cdc.gov/legionella/index.html.) Hazard analyses and critical control points (HACCP), an industry method designed to improve food safety, can be applied to Legionella prevention – as outlined by forthcoming practices from the American Society of Heating, Refrigerating and Air-Conditioning Engineers, Inc. (ASHRAE) Standard Project Committee 188 (http://spc188.ashraepcs.org/). Facility managers may also consider periodic environmental monitoring of the potable water system to identify Legionella colonization in the context of a full HACCP plan. When possible, potable water systems should be designed to minimize the potential for Legionella colonization (e.g., short, direct pipes with appropriate insulation and materials).
In facilities known to be colonized, remediation measures to protect vulnerable residents are indicated and often involve halogen-based disinfectants, such as chlorine or chlorine dioxide [24–26]. Alternatively, permanent elevation of water heater temperatures (>130°F/ >54.4°C) can reduce Legionella viability , but concerns for scalding among older individuals  may prevent this approach from being a feasible option without safeguards (e.g., thermostatic mixing valves). Facilities with Legionella colonization should also adhere to the ASHRAE guidelines for minimizing legionellosis risk .
If LD cases have been detected among residents, exposure reduction, heightened awareness, and clinical surveillance  should be accomplished through coordination among facility managers, healthcare providers, caregivers, and public health officials. To reduce exposure when potable water is implicated, we found that bathing in a tub appeared to be protective. Because some residents may have bathed in a tub and showered periodically, we may have underestimated the true protective effect of exclusive tub bathing. The finding that tub bathing is protective is plausible because it can reduce continuous exposure to water aerosols, which would otherwise be experienced while showering. Other measures to minimize contact with aerosolized potable water, including exposure reductions during dishwashing or cleaning of kitchens, bathrooms, or other areas, also should be evaluated and promoted. If a dishwasher is unavailable, for example, a sink could be filled with running water while positioning oneself a distance away, as an alternative habit that may be effective in avoiding repeated inhalation of aerosolized water when dishes are washed individually. To heighten awareness for early detection of LD, information on signs and symptoms of acute respiratory disease and pneumonia, and recommendations for immediate healthcare-seeking, should be provided to residents and family members as well as medical directors, nurses, infection control professionals, and other caregivers. Added effort may be required to communicate effectively among older adults with varying degrees of health literacy, dementia, and other challenges. Socioeconomic, ethnic/cultural, and language barriers may also need to be recognized. Finally, clinical surveillance can be accomplished through specific diagnostic testing and systematic monitoring for symptoms of acute illness. Urinary antigen testing is indicated for suspected L. pneumophila serogroup 1 infections, which represent the majority (~84%) of LD cases in the United States . Caregivers should also promptly recognize and refer residents with acute, febrile respiratory illness to healthcare providers.
The clinical presentation of LD pneumonia can be atypical, particularly among elderly patients [6, 30]. Therefore, a heightened index of suspicion among clinicians and healthcare providers is also indicated to accelerate diagnosis and effective treatment of Legionella pneumonia among residents and visitors to facilities with colonization or the occurrence of LD cases. In addition to Legionella urine antigen testing, clinicians should attempt to recover respiratory secretions for Legionella culture from any patient linked to an outbreak and any patient hospitalized with severe community-acquired pneumonia of unknown etiology because clinical Legionella isolates are critical for establishing an association with an environmental exposure and can direct appropriate antimicrobial therapy (e.g., levofloxacin). Healthcare providers should also work closely with patients to eliminate modifiable risk factors for pneumonia (e.g. smoking) , optimize the management of underlying medical conditions (e.g., asthma, diabetes mellitus), and educate patients on behaviors that reduce exposures to aerosolized water.
Managers of elderly-housing facilities, local public health officials, and other stakeholders should implement Legionella prevention and control strategies based on whether Legionella colonization of potable water has been detected and especially when LD cases occur. Physicians specializing in infectious diseases and other persons providing healthcare services to elderly residents should be aware of the increased risk of LD in this population; awareness is a prerequisite for the provision of quality healthcare, including prompt diagnosis and effective treatment as well as counseling on the importance of risk modification and exposure reduction to prevent additional morbidity and mortality.
Numerous microbiologists contributed to the investigation, including Maria Carlos, Gonzalo Crujeiras, Vanlila Patel, and Leena Trivedi (Maryland Department of Health and Mental Hygiene) and Maja Kodani, Claressa Lucas, Kathleen Thurman, and Genyan (Patrick) Yang (CDC). Alvina Chu (Maryland Department of Health and Mental Hygiene) and Matt Moore (CDC) coordinated aspects of the field investigation. Felicita David, Jennifer Loo, Rebecca Roberts, Karrie-Ann Toews, and Carolyn Wright (CDC) provided data management. Tim Keene (Legionella Risk Management) and Joe Carpenter and Tom Taylor (CDC) consulted during the environmental investigation. Many volunteers assisted the epidemiological investigation. We thank the facility managers and residents who collaborated with the investigation.
- Marston BJ, Plouffe JF, File TM, Hackman BA, Salstrom SJ, Lipman HB, Kolczak MS, Breiman RF: Incidence of community-acquired pneumonia requiring hospitalization. results of a population-based active surveillance study in Ohio. the community-based pneumonia incidence study group. Arch Intern Med. 1997, 157: 1709-1718. 10.1001/archinte.1997.00440360129015.View ArticlePubMedGoogle Scholar
- Benin AL, Benson RF, Besser RE: Trends in legionnaires disease, 1980–1998: declining mortality and new patterns of diagnosis. Clin Infect Dis. 2002, 35: 1039-1046. 10.1086/342903.View ArticlePubMedGoogle Scholar
- Gutierrez F, Masia M, Mirete C, Soldan B, Rodriguez JC, Padilla S, Hernandez I, Royo G, Martin-Hidalgo A: The influence of age and gender on the population-based incidence of community-acquired pneumonia caused by different microbial pathogens. J Infect. 2006, 53: 166-174. 10.1016/j.jinf.2005.11.006.View ArticlePubMedGoogle Scholar
- Neil K, Berkelman R: Increasing incidence of legionellosis in the United States, 1990–2005: changing epidemiologic trends. Clin Infect Dis. 2008, 47: 591-599. 10.1086/590557.View ArticlePubMedGoogle Scholar
- Marston BJ, Lipman HB, Breiman RF: Surveillance for legionnaires' disease. risk factors for morbidity and mortality. Arch Intern Med. 1994, 154: 2417-2422. 10.1001/archinte.1994.00420210049006.View ArticlePubMedGoogle Scholar
- Sopena N, Pedro-Botet L, Mateu L, Tolschinsky G, Rey-Joly C, Sabria M: Community-acquired Legionella pneumonia in elderly patients: characteristics and outcome. J Am Geriatr Soc. 2007, 55: 114-119. 10.1111/j.1532-5415.2006.01021.x.View ArticlePubMedGoogle Scholar
- Gacouin A, Le Tulzo Y, Lavoue S, Camus C, Hoff J, Bassen R, Arvieux C, Heurtin C, Thomas R: Severe pneumonia due to Legionella pneumophila: prognostic factors, impact of delayed appropriate antimicrobial therapy. Intensive Care Med. 2002, 28: 686-691. 10.1007/s00134-002-1304-8.View ArticlePubMedGoogle Scholar
- Heath CH, Grove DI, Looke DF: Delay in appropriate therapy of Legionella pneumonia associated with increased mortality. Eur J Clin Microbiol Infect Dis. 1996, 15: 286-290. 10.1007/BF01695659.View ArticlePubMedGoogle Scholar
- Seenivasan MH, Yu VL, Muder RR: Legionnaires' disease in long-term care facilities: overview and proposed solutions. J Am Geriatr Soc. 2005, 53: 875-880. 10.1111/j.1532-5415.2005.53270.x.View ArticlePubMedGoogle Scholar
- U.S. Department of Housing and Urban Development: Elderly Housing Consumption: Historical Patterns and Projected Trends. [http://www.huduser.org/530datasets/ahs/elderly_housing_consumption.pdf], accessed June 26, 2013
- Stevenson DG, Grabowski DC: Sizing up the market for assisted living. Health Aff (Millwood). 2010, 29: 35-43. 10.1377/hlthaff.2009.0527.View ArticleGoogle Scholar
- CDC: Procedures for the recovery of Legionella from the environment. US Department of Health and Human Services, Public Health Service. 1994, 1-13.Google Scholar
- Sanden GN, Cassiday PK, Barbaree JM: Rapid immunodot technique for identifying Bordetella pertussis. J Clin Microbiol. 1993, 31: 170-172.PubMedPubMed CentralGoogle Scholar
- Joly JR, McKinney RM, Tobin JO, Bibb WF, Watkins ID, Ramsay D: Development of a standardized subgrouping scheme for Legionella pneumophila serogroup 1 using monoclonal antibodies. J Clin Microbiol. 1986, 23: 768-771.PubMedPubMed CentralGoogle Scholar
- Gaia V, Fry NK, Afshar B, Luck PC, Meugnier H, Etienne J, Peduzzi R, Harrison TG: Consensus sequence-based scheme for epidemiological typing of clinical and environmental isolates of Legionella pneumophila. J Clin Microbiol. 2005, 43: 2047-2052. 10.1128/JCM.43.5.2047-2052.2005.View ArticlePubMedPubMed CentralGoogle Scholar
- Ratzow S, Gaia V, Helbig JH, Fry NK, Luck PC: Addition of neuA, the gene encoding N-acylneuraminate cytidylyl transferase, increases the discriminatory ability of the consensus sequence-based scheme for typing Legionella pneumophila serogroup 1 strains. J Clin Microbiol. 2007, 45: 1965-1968. 10.1128/JCM.00261-07.View ArticlePubMedPubMed CentralGoogle Scholar
- European Working Group for Legionella Infections: M13 Variant of the Sequence-Based Typing (SBT) protocol for epidemiological typing of Legionella pneumophila. [http://www.hpa-bioinformatics.org.uk/legionella/legionella_sbt/php/sbt_homepage.php]
- Edelstein PH, Edelstein MA: Intracellular growth of Legionella pneumophila serogroup 1 monoclonal antibody type 2 positive and negative bacteria. Epidemiol Infect. 1993, 111: 499-502. 10.1017/S095026880005723X.View ArticlePubMedPubMed CentralGoogle Scholar
- Kozak NA, Benson RF, Brown E, Alexander NT, Taylor TH, Shelton BG, Fields BS: Distribution of lag-1 alleles and sequence-based types among Legionella pneumophila serogroup 1 clinical and environmental isolates in the United States. J Clin Microbiol. 2009, 47: 2525-2535. 10.1128/JCM.02410-08.View ArticlePubMedPubMed CentralGoogle Scholar
- Tijet N, Tang P, Romilowych M, Duncan C, Ng V, Fisman DN, Jamieson F, Low DE, Guyard C: New endemic Legionella pneumophila serogroup I clones, Ontario, Canada. Emerg Infect Dis. 2010, 16: 447-454. 10.3201/eid1603.081689.View ArticlePubMedPubMed CentralGoogle Scholar
- Liang JL, Dziuban EJ, Craun GF, Hill V, Moore MR, Gelting RJ, Calderon RL, Beach MJ, Roy SL: Surveillance for waterborne disease and outbreaks associated with drinking water and water not intended for drinking–United States, 2003–2004. MMWR Surveill Summ. 2006, 55: 31-65.PubMedGoogle Scholar
- Phares CR, Russell E, Thigpen MC, Service W, Crist MB, Salyers M, Engel J, Benson RF, Fields B, Moore MR: Legionnaires' disease among residents of a long-term care facility: the sentinel event in a community outbreak. Am J Infect Control. 2007, 35: 319-323. 10.1016/j.ajic.2006.09.014.View ArticlePubMedGoogle Scholar
- ASHRAE: Minimizing the risk of legionellosis associated with building water systems. 2000, Atlanta, GA: ASHRAE Guideline 12–2000Google Scholar
- Kim BR, Anderson JE, Mueller SA, Gaines WA, Kendall AM: Literature review–efficacy of various disinfectants against Legionella in water systems. Water Res. 2002, 36: 4433-4444. 10.1016/S0043-1354(02)00188-4.View ArticlePubMedGoogle Scholar
- Moore MR, Pryor M, Fields B, Lucas C, Phelan M, Besser RE: Introduction of monochloramine into a municipal water system: impact on colonization of buildings by Legionella spp. Appl Environ Microbiol. 2006, 72: 378-383. 10.1128/AEM.72.1.378-383.2006.View ArticlePubMedPubMed CentralGoogle Scholar
- Srinivasan A, Bova G, Ross T, Mackie K, Paquette N, Merz W, Perl TM: A 17-month evaluation of a chlorine dioxide water treatment system to control Legionella species in a hospital water supply. Infect Control Hosp Epidemiol. 2003, 24: 575-579. 10.1086/502254.View ArticlePubMedGoogle Scholar
- Katz SM, Hammel JM: The effect of drying, heat, and pH on the survival of Legionella pneumophila. Ann Clin Lab Sci. 1987, 17: 150-156.PubMedGoogle Scholar
- CDC: Nonfatal scald-related burns among adults aged ≥65 years --- United States, 2001--2006. MMWR Morb Mortal Wkly Rep. 2009, 58: 993-996.Google Scholar
- Yu VL, Plouffe JF, Pastoris MC, Stout JE, Schousboe M, Widmer A, Summersgill J, File T, Heath CM, Paterson DL, et al: Distribution of Legionella species and serogroups isolated by culture in patients with sporadic community-acquired legionellosis: an international collaborative survey. J Infect Dis. 2002, 186: 127-128. 10.1086/341087.View ArticlePubMedGoogle Scholar
- Sugihara E, Dambara T, Aiba M, Okamoto M, Yonemitsu J, Sonobe S, Koga H, Inui A, Hada N, Matsumoto N, et al: Clinical characteristics of 8 sporadic cases of community-acquired Legionella pneumonia in advanced age. Intern Med. 2007, 46: 461-465. 10.2169/internalmedicine.46.6084.View ArticlePubMedGoogle Scholar
- The pre-publication history for this paper can be accessed here:http://www.biomedcentral.com/1471-2334/13/291/prepub
This article is published under license to BioMed Central Ltd. This is an Open Access article distributed under the terms of the Creative Commons Attribution License (http://creativecommons.org/licenses/by/2.0), which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.